Fan shall be a direct drive, wall mounted, propeller exhaust or supply fan.
Fan shall be of riveted and bolted construction utilizing corrosion resistant fasteners. The unit shall include a heavy gauge G90 galvanized steel fan panel with an integral venturi. The fan panel shall have pre-punched mounting holes for ease of installation. The fan shall bear a permanently attached nameplate displaying model and serial number of unit for future identification. The unit shall be factory tested after assembly.
Precision pitched propeller shall be fabricated steel or cast aluminum blades attached to a heavy duty hub. The hub shall be securely fastened to the motor shaft utilizing two setscrews or split tapered bushings. Propeller shall be balanced in accordance with AMCA Standard 204-96, Balance Quality and Vibration Levels for Fans.
Motors & Electrical:
Motor shall be heavy-duty type with permanently lubricated sealed bearings furnished at the specified voltage, phase, and enclosure. Motors should be nationally recognized brands either open drip-proof, totally enclosed, or explosion proof.
Options and Accessories:
Optional accessories shall be provided either factory installed or field installed as detailed in the fan schedules.
Fan shall be listed by Underwriters Laboratories (cULus 705), for US and Canada when specified in the fan schedule.
The equipment is warranted to be free from defects in materials and workmanship, under normal use and service, for a period of 24 months from the date of shipment.
Fan shall be model F-AWPD as manufactured by FloAire